Question: I have a lot of alcohol-based hand sanitizer on hand, due to the pandemic. Is there anything special about storage or placement of dispensers that I should know?
Answer: Yes, alcohol-based hand sanitizer that is greater than 20% alcohol falls under a Class 1B flammable liquid according to the National Fire Protection Association (NFPA). Here are some requirements to consider:
- Individual dispensers located in a hallway must be 0.5 gallons or less (no gallon jugs).
- Dispensers must be installed at least 1 inch away from electrical receptacles and light switches and must be separated from another dispenser by at least 4 feet horizontally.
- Dispensers must not be installed above carpeted floors, unless the area is sprinklered.
- Automatic dispensers (touch free) are required to be tested each time they are refilled, can only activate when the object is within 4 inches of the dispenser and will only dispense the amount required as determined by the United States FDA.
- The Ohio Fire Code requires the storage of more than 10 gallons in a flammable liquid cabinet or flammable liquid storage room. The NFPA 30 code dictates storage considerations starting at 5 gallons. No storage is permitted in basements.
If you have specific questions about safe storage and handling, consult the Safety Data Sheet for the product or call your local Authority Having Jurisdiction for fire code enforcement.
*Provided by the Ohio BWC safety consultants.
You must be logged in to post a comment.